NFPA 25 Obstruction Investigations – Consulting & Repair in Maine, New Hampshire, Vermont & Massachusetts
About Five Year Obstruction Investigations
Sprinkler systems are mechanical systems that require ongoing inspections and maintenance to help keep them in optimal working condition. Over time these systems can accumulate organic or inorganic materials inside the pipe and valves. Piping, valves and other devices can even become obstructed by these materials which can cause system failure in the event of an emergency. This build-up also prematurely deteriorates and weakens the piping.
In 2002, NFPA recognized that this internal build-up compromised the integrity of the sprinkler system and posed a significant risk to life and property. Code was added to require five year internal obstruction investigations of fire protection system piping to identify sources of materials that could cause blockage and deteriorate the system. The obstructing materials can come in the form of MIC (microbiologically influenced corrosion), slime, sludge, flakey scale or even a hard packed cement like substance.
Sprinkler Systems Inspection Corp. has knowledgeable and experienced staff ready to help you develop a program for code compliance and maintaining your system in working order. Internal inspections of piping are performed by licensed inspectors. Full reports with accompanying photos are supplied to help monitor the health of your system. Should a problem be found, our professional staff is ready to offer guidance and solutions. Contact us for an estimate today.
NFPA 25, 14.2.1 An inspection of piping and branch line conditions shall be conducted every five years by opening a flushing connection at the end of one main and by removing a sprinkler toward the end of one branch line for the purpose of inspecting for the presence of organic or inorganic material.